Honeywell Security Intrusion and Communications, ADEMCO, AlarmNet, IntelliSense, Apex, FBII, electronic security systems, burglary alarms and fire alarms for. Installation manual for the Honeywell wireless three-zone sensor. For help installing your , call The Honeywell is a wireless three zone sensor. Unlike other Honeywell wireless window and door sensors, the does not have an internal reed switch.
|Published (Last):||1 March 2016|
|PDF File Size:||7.5 Mb|
|ePub File Size:||9.59 Mb|
|Price:||Free* [*Free Regsitration Required]|
Seller does not represent that the product s it sells may not be compromised or circumvented; that the product s will prevent any personal injury or property loss by burglary, robbery, fire or otherwise; or that the product s will in all cases provide adequate warning or protection. The locking tab will click as the case back locks in place. Install the mounting plate, with its case holding posts pointing up in this examplein the.
Disengage the supplied mounting plate from the unit by inserting the blade of a small. A built-in cover tamper switch is activated when the cover is removed.
Mounting For proper orientation of the unit in relation to its wall mounting plate and the loop wiring, read all of this section before installing the unit. Surface wiring should enter via the thin “breakout” area provided in.
Seller’s obligation shall be limited to repairing or replacing, at its option, free of charge for materials or labor, any product s which is proved not in compliance with Seller’s specifications or proves defective in materials or workmanship under normal use and service. Dispose of used batteries promptly.
Observe correct polarity and insert the battery provided into the battery holder see. Remove the transmitter’s 587 if not already off as described in Mounting Step 1. Regular maintenance and inspection at least annually by the installer and frequent testing by.
The unit may, however, be installed in any direction, as long as the relationship of ademc unit to its mounting plate is ademvo. Page of 2 Go. Don’t have an account? For UL installations, no contact in any of the loops may be more than 3 feet from the transmitter. The has its own unique identification codes permanently assigned during manufacture. The two Auxiliary Loops are closed-circuit, with a nominal response time of mSec.
To replace the cover, engage the hooks along one edge and snap shut. Got it, continue to print. Complain wrong Brand wrong Model non readable.
Attach the case back to the mounting plate by sliding the keyhole slots in the case back down. If a contact loop is not to be used, no connection is needed across its terminals.
Except in the case of the position 4 ON setting, the Auxiliary loops are not affected by. The installer should assume the responsibility of developing and offering a regular maintenance. Comments to this Manuals Your Name. When a satisfactory location is found, remove the battery and proceed with installation. With the battery still not inserted, connect the loop wiring to the unit’s terminals see Diagram 2.
No increase or alteration, written or verbal, of the obligations of this Limited Warranty is authorized. The description that follows assumes that the unit will be mounted as shown in the diagrams. Add to my manuals Add. Although two holes are provided in the unit that would permit mounting directly to a surface holes “A” in Diagram 2it is recommended that the mounting plate be used, as described below, for ease in removing the unit for servicing should it become necessary.
If concealed wiring is to be used, feed it through the slot in the case back but do not connect. Customer understands that a properly installed and maintained alarm system may only reduce the risk of a burglary, robbery, fireor other events occurring without providing an alarm, but it is not insurance or a guarantee that such will not occur or that there will be no personal injury or property loss as a result.
Recommendations must be included for a specific. The should be treated as “RF” i. This warranty replaces any previous warranties and is the only warranty made by Seller on this product s. To print the manual completely, please, download it.
Wiring Connections; Specifications – Honeywell ADEMCO Installation And Setup Manual [Page 2]
By pressing ‘print’ button you will print only current page. Disengage the supplied mounting plate from the unit by inserting the blade aedmco a small screwdriver into the locking tab release window see Diagram 2 and pressing it against the case locking tab see Diagram 1 while sliding the plate downward along the case back.
The open slot at the other end of the unit cannot be used as a cover pry-off. Seller shall have no obligation under this Limited Warranty or otherwise if the product s is altered or improperly repaired or serviced by anyone other than Honeywell factory service.
Honeywell ADEMCO 5817 User Manual
For this application, the alignment guide strip along one edge of the plate serves no function and may be broken away, if desired. Adeemco of fire, explosion, and burns. While the transmitter is being enrolled by the control, all DIP switch positions should. The Primary Loop has several DIP switch selectable options that determine its connection requirements, response, and transmission characteristics see DIP switch setting table on next page.
Do not recharge, disassemble, heat above. Don’t show me this message again. Enter text from picture: Replace battery only with: For UL installations with fire zones, the position 4 ON setting must not be used. If concealed wiring is to be used, feed the wires through the concealed wiring entry hole at. Each loop transmits a unique ID code to a wireless system receiver connected to the system control panel. It is not necessary to program the transmitter IDs during installation.
The Multi-Point Universal Transmitter may have three contact loops addemco to it.